Thank you for your purchasing “Fuji Digital Temperature Controller.” Please exactly the one you ordered and use it according to the following instructions. Terminal block protecting cover. SSR. Manual Operation key output up key output down. SSR drive output. Heater. Boiler. Temperature Input.  Features. PXR4. Buy Fuji PXR4 PID Temperature Controller, 48 x 48 (1/16 DIN)mm, 2 Output Relay, V ac, V ac Temperature Controller PXR-Series_Software – Manual.
|Published (Last):||20 September 2012|
|PDF File Size:||4.59 Mb|
|ePub File Size:||2.20 Mb|
|Price:||Free* [*Free Regsitration Required]|
Page 34 [Table 4] Alarm action type code Parameter: Add to my manuals Add.
Error Indications Error indications Error indications This controller has a display function to indicate several types of error code fhji below. Got it, continue to print.
Reverse operation Parameter Setting value Combination of alarm functions Please see the table as shown below. Check Of Specifications And Accessories Check of specifications and accessories Before using the controller, check if the type and specifications are as ordered. Page 30 q Select the type of control output action.
Fuji Electric PXR4 Instruction Manual
Shift to operating condition Operation mode Press the once. Page 14 Switching by Fhji setting mode Parameter settings Parameter selection Press the for 2 sec. Page 32 [Table 1] Input type code Parameter: However, depending on setting of “P-n1”, control action, control outputs are provided at the abnormal input.
Suggesting that the user’s mishandling can Warning A table of Model code configuration is given in Page Set the hysteresis to avoid chattering. The controller is horizontal. Thank you for your purchasing “Fuji Digital Temperature Controller”. Digital input DI function [option] Page 4 Warning 1. Vertical mounting, flush on the panel. Error code Possible cause Control output Page 21 4 Self-tuning is executed by any of the following conditions.
Safety precautions must be taken by every user to prevent accidents. Micro-controller X Sales Div. However, we are not liable for direct and indirect. Safety Precautions Safety Precautions Before using this product, the user is requested to read the following precautions carefully to ensure the safety.
Check of specifications and accessories Page 38 — 38 — For details, see Table 4, Alarm action type codes on page 4. ENCDA power supply voltage: Connect it between contacts of the relay control output.
Micro Controller X Operation Manual Model PXR4,5,9 (ECNO f) | Fuji Electric Corp. of America
Setting of input type and control algorithm We paid the utmost care for the accuracy of the contents. Please check that the product is exactly the.
If necessary to appear these parameters, please refer to the following procedure. It is useful where modification of PID parameters is required repeatably due to frequent change in process condition. Page 23 Combination of alarm functions Please see the table as shown below. Output Control outputs 1 and 2 and alarm outputs all are not provided.
Switching by Parameter setting mode Parameter settings Parameter selection Press the for 2 sec. Check of specifications and accessories Before using the controller, check if the type and specifications are as ordered. If any of the error codes is displayed, please eliminate the cause of error immediately.
Usually it is not necessary to change the setting.
FUJI ELECTRIC PXR4 INSTRUCTION MANUAL Pdf Download.
Page 35 [Table 5] Control operation type code Parameter: Page 33 [Table 3] Input range Manial range Parameter: The contents of this ufji may be changed in the future without prior notice. Comments to this Manuals Your Name. Page of 38 Go. Dealers are cordially requested to ensure the delivery of this Instruction Manual to hands of the end.
Safety Precautions Before using this product, the user is requested to read the following precautions carefully to ensure the safety.